Color Temperature: 3000K warm white WW /5000K cool white CW Lumens:500lm Beam Angle: 110º Dimmable Power: 9W Frequency: 60Hz CRI: 80 PF: 0.95 Volts: 120V AC Life: 50000Hrs
Suitable for damp locations.
Suitable for insulated ceiling Type IC Rated for direct contact with insulation.
1.Risk of electric shock- turn off power before inspection, installation or removal.
2.Locate a suitable position to place the LED fixture and open a hole in accordance to the cut-hole dimensions (refer to Hole Cut Table for appropriate size).
3.Run the electrical wire from the switch (power supply), through the mounting hole-use NMD90 OR BX cable.
4.Open the hardwire box swing cover and remove the appropriate knockout(s).
5.Insert the electrical supply cable through the knockout.
6.Wire box using supplied quick connect push-in terminals. Connect green ground wire of cable to green wire of box. Connect white wire of cable to white wire of box. Connect black wire of cable to black wire of box.(Fig. 1).
7.Place all wiring and connections back into the box and close the cover.
8.New construction applications: Junction box shall be firmly secured to studs, joists, or similar fixed structural units.(Fig.2)
9. Remodel applications: Do not require the junction box to be firmly secured after the mounting plates, studs, joists, or structural units that have been concealed. Snap off the junction box tabs(Fig.3), then insert into ceiling(Fig.4).
10.Push spring loaded clips on the fixture upwards and insert fixture base into the mounting hole. Release the clips and fixture will be pulled flush to the ceiling(Fig.5).
11.Once assembly is complete, turn on power to confirm fixture is working properly. Hole Cut Size:∅4-3/32"104mm
Tools Required: Saw Measuring Tape Electrical Wiring (use type and gauge suitable for application to connect the fixtures).
SAFETY: For your safety, this fixture must be wired in accordance to local electrical codes and ordinances. All work should be done by a qualified electrician.
Warning: Make sure power is OFF from the electrical panel before starting installation or attempting and maintenance. For indoor installation only.
For WET location applications, after fixture is installed on ceiling, put silicone glue to seal the gap between fixture and ceiling.